|Place of Origin:||Yuhuan Zhejiang China|
|Minimum Order Quantity:||3000|
|Delivery Time:||35 work days|
|Payment Terms:||T/T, L/C|
|Supply Ability:||3000pcs-100000pcs it only takes 35 days|
|Valve Body:||Brass||Valve Ball:||Brass|
|Hand:||Iron||Sealing Ring Of Ball:||PTFE|
Ball valve installation&application instruction
1.Range of application
The ball valve is mainly used for cutting off, distributing and changing the direction of the flowmedium in the pipeline. To prolong the service life of the ball valve, full open and full close are highlysuggested.
2.Main technical parameters of the product
2-1. we select high quality cooper material and apply hot forging process in the production process.2-2. The main working medium are wter,il,gas,etc.
2-3. working temperature range from -10'Cto 120C
2-4. each nominal working pressure of our ball valve are 2. 5Mpa,2.0Mpa and 1.6Mpa
3-1. For pipe thread connection type ball valve,we should make sure the pipe being vertical againstthe end surface of the valve body when tighten the connection part.our special warning is that weshould only wrench the octagonal at the same end of body instead of the other side to avoid
deformation so as to affect its normal open function.
3-2. For internal thread type ball valve,we should control the length of the external thread at the pipeend in case deformation of the valve body caused by the external thread's aqueezing the surface ofthe internal thread so as to affect leakproofness
3-3. When connecting the pipe thread type ball valve with pipe thread,the internal thread can beeither tapered pipe thread or cylindrical pipe thread,but the external thread must be tapered pipethread,otherwise it will cause leakage due to loose connection.
3-4. When intallilgn the pipe thread type ball valve,the sealing material must be clean.
3-5. Such obstacles as wall,coupling nut and pipe should not be placed inside the open/close range .3-6. When the ball valve handle is parallel to the body,it is open,otherwise,it is close.
3-7. The working medium should not contain particles,corrosive gas or liquid
3-8. PP-R ball valve installation instruction:
3-8-1. Remove the coupling nut,PP-R pipe and O-ring from the valve body
3-8-2. Pull the coupling nut on the pipe in the original direction
3-8-3. join the PP-R flange with PP-R pipe with a hot fusion machine.Pull the O-ring in thePP-R flange when it cooled down.Last,tighten the coupling nut with valve body.
Butterfly handle ball valve
|Sealing Ring Of Ball||PTFE|
|Product size parameters|
|DN15||M 1/2"||F 1/2"||15||87.5||45.8||59.5|
|DN20||M 3/4"||F 3/4"||20||87.5||49||64.5|
|DN25||M 1"||F 1"||25||104||58||76.5|
|DN32||M 1-1/4"||F 1-1/4"||32||136||69.5||85.2|
|DN40||M 1-1/2"||F 1-1/2"||37||150||76.5||100|
|DN50||M 2"||F 2"||47||150||93||114.5|
|DN15||M 1/2"||F 1/2"||15||50||42||59.5|
|DN20||M 3/4"||F 3/4"||20||50||45.5||64.5|
|DN25||M 1"||F 1"||25||62||56.5||76.5|
Contact Person: Joe