|Temperature Of Media:
|G1/2" - G2''
|Standard Or Nonstandard:
|Brass Ball Valve
|-10°C To 120°C
|Brass Thread Ball Valve
TMOK Threaded Brass Ball Valve,
BSP Thread Brass Ball Valve,
Yellow Handle Brass Ball Valve
TMOK Factory Direct Female And Female Thread BSP Thread Brass Ball Valve With Yellow Handle
Ball valve installation&application instruction
1. Range of application
The ball valve is mainly used for cutting off, distributing and changing the direction of the flow medium in the pipeline. To prolong the service life of the ball valve, full open and full close are highly suggested.
2. Main technical parameters of the product
2-1. we select high quality copper material and apply hot forging process in the production process.
2-2. The main working medium are water,oil,gas,etc.
2-3. working temperature range from -10℃-120℃
2-4. each normal working pressure of our ball valve are 2. 5Mpa,2.0Mpa and 1.6Mpa
3. Installation manual
3-1. For pipe thread connection type ball valve,we should make sure the pipe being vertical against the end surface of the valve body when tighten the connection part.our special warning is that we should only wrench the octagonal at the same end of body instead of the other side to avoid
deformation so as to affect its normal open function.
3-2. For internal thread type ball valve,we should control the length of the external thread at the pipe end in case deformation of the valve body caused by the external thread's aqueezing the surface of the internal thread so as to affect leakproofness
3-3. When connecting the pipe thread type ball valve with pipe thread,the internal thread can be either tapered pipe thread or cylindrical pipe thread,but the external thread must be tapered pipethread,otherwise it will cause leakage due to loose connection.
3-4. When intallilgn the pipe thread type ball valve,the sealing material must be clean.
3-5. Such obstacles as wall,coupling nut and pipe should not be placed inside the open/close range .
3-6. When the ball valve handle is parallel to the body,it is open,otherwise,it is close.
3-7. The working medium should not contain particles,corrosive gas or liquid
3-8. PP-R ball valve installation instruction:
3-8-1. Remove the coupling nut,PP-R pipe and O-ring from the valve body
3-8-2. Pull the coupling nut on the pipe in the original direction
3-8-3. Join the PP-R flange with PP-R pipe with a hot fusion machine.Pull the O-ring in the PP-R flange when it cooled down.Last,tighten the coupling nut with valve body.
|Temperature Of Media
|Brass Ball Valve
|Thread Ball Valve
|Single Gross Weight
|Medium Pressure, PN16
|ISO9001 2015 CE
|Standard Or Nonstandard
|Single Package Size
|STANDARD OR AS YOUR REQUIREMENT
Contact Person: Cindy